While many people may logically conclude that acetylene is stored in standard high-pressure cylinders which are hollow in construction and gas storage use, this point is not true. Acetylene cylinders are a separate, dedicated, and special type of cylinder that is used to store and transport the gas above pressures of 5 psi (.3 bar). A standard acetylene cylinder has a length of 30” (76.2 cm) and has a 10” (24.4 cm) diameter.
Instructions for Storing Acetylene Cylinders
1. General Storage Guidelines:
a. Always use and/or have access to protective clothing and equipment when handling the cylinders. These include gloves, goggles, cotton clothing, and fire extinguishers.
b. Always work with, or under the supervision of qualified personnel.
c. Keep cylinders away from any kind of flammable substance.
d. Acetylene cylinders should always be stored upright, with the valve end in the upward position.
e. The cylinder valve should always be kept closed when not in use and the fuse plug(s) should be checked to verify a tight seal.
f. The cylinders should never be stored in extreme temperature environments. In warm environments, the temperature should never exceed 125℉ (52℃). In freezing temperatures, the pressure may drop within the cylinder to nearly zero and when flowed, acetone may leak from the cylinder resulting in clogging of downstream equipment such as a regulator.
g. Empty and filled acetylene cylinders should be stored separately as well.
h. Acetylene cylinders should be stored separately from cylinders containing other gases.
i. The cylinders need to be protected from potential mechanical and physical damages.
2. Indoor Storage:
a. The storage area should have a fire resistance rating of 2h. (This is the rating for flammable gases.)
b. The area should have the requisite amount of ventilation, however, it should also prevent gas migration within the building.
c. Acetylene storage areas should meet Class 1, Division 1, Group A ratings with all equipment in the area meeting this classification.
d. The cylinders should be stored in an area that is at least 1 meter away from elevators, ramps, fire exits, stairways, passages, and corridors.
3. Outdoor Storage:
a. Fencing at least 71” (1.8 meters) high to prevent unauthorized entry.
b. Lockable (and locked) gates when the area is not in use.
c. The enclosed area should be various distances from any building depending on the amount of acetylene stored:
1. Less than 6003 ft3 (170 m3) capacity: 5’ (1.5 meters)
2. Between 6004 ft3 (170 m3) and 17,657 ft3 (500 m3) capacity: 25’ (7.5 meters)
3. Greater than 17,657 ft3 (500 m3) capacity: 50’ (15 meters)
These various points will help users of acetylene cylinders to ensure proper cylinder handling and storage while reducing the chances of explosions.
If you are note clear and/or require more information, it is always best to consult a qualified technician prior to handling and storing your acetylene cylinders.