Our Acetylene plants are manufactured with complete in-house know how. Every part has been carefully designed by experienced engineers. These parts are made of the best material. Every part has been accurately made and carefully inspected before assembly. Each unit, after assembly, is charged and worked continuously to check its performance. You are, therefore, assured of an efficient and dependable Acetylene Gas Plant.
Our Acetylene Plant is of an advanced design, incorporating several features not ordinarily found in other generators enabling them to attain the highest efficiency in the world — that is 98%. They are fully automatic plants with twin hopers and needs an operator's attention for only ten minutes in an hour.
All operations are performed by pneumatically controlled valves, assisted by highly sensitive sensors, integrated with the temperature control instruments. These in turn open the water inlet valve or residue drain valve .Two pneumatic operated cylinders help to open and close the feed of calcium carbide which is fed into the generator by screw feed conveyors. The screw feed mechanism and the agitator are operated by flame-proof motors and fittings. The entire operation is perfectly synchronized to give maximum efficiency and simplicity in operation. Any failure, whether it is of power supply, water, instruments, air is signaled visually as well as audibly when an alarm bell rings to alert the operator.
The design of the entire plant has been made keeping the utmost safety in mind. Auto controls, flash back arrestors, high pressure reverse flow check valves, safety valves and complete visual gauging helps to protect both equipment and personnel.
Description of components of the Acetylene plant.
1. Acetylene Gas Generator:
The IIGAS Acetylene Generator and Acetylene Gas Cylinder are advanced design, incorporating several features not ordinarily found in other generators and cylinders. The IIGAS Acetylene generator is fully automatic. Pneumatically controlled valves and highly sensitive sensors, integral with the temperature control instruments, perform all operations. These, in turn, open the water inlet valve or residue drain valve etc. Two hydraulic pumps help to open and close the supply of calcium carbide, which is fed into the generator by screw feed conveyors. The screw feed mechanism and the agitators are operated by flameproof motors and fittings. The entire operation is perfectly synchronized to achieve maximum efficiency and simplicity in operation. Any failure, whether it is of power supply, water or air is signaled visually and also audibly when an alarm bell rings to alert the operator.
The IIGAS Acetylene Generator can be set to operate at a given temperature, regardless of the size of carbide used or temperature of the cooling water, A sensitive sensor actuates a pneumatic control that adds water into the generator tank when the temperature exceeds the set limit, thus maintaining a given standard temperature. This helps in complete utilization of carbide, which is a very expensive raw material.
If all the gas generated cannot be drawn in by the compressor and passed on the filling manifold, either due to low capacity of the compressor or fast generation, gas pressure will gradually build in the generator. When the gas pressure reaches a predetermined level carbide charging will be cut off automatically and further generation of gas is stopped. There is no expensive gas holder with the IIGAS Acetylene Generator. This item alone will reduce the investment in such a plant. Further, as the gas generated is always at a positive pressure, the pumping cost is also reduced. Since the generator is constantly at a positive pressure, (once the plant has been purged with Nitrogen) no air can enter the system, and it is this feature which makes the "IIGAS" Plant inherently very safe.
Water Level Control:
If excessive water enters the generator to cool it and the water level goes above the high-level mark, the water-level control instrument will immediately discharge the excessive water thus maintaining the level between the acceptable high and low-level marks.
No loss -Carbide charge:
No gas is lost or wasted while charging the carbide because one section is completely sealed off from the generator by a high pressure hydraulically operated valve. All the above controls are automatic and require no attention from the operator.
The Acetylene gas leaving the generator is hot and carries with it some water vapor and other impurities. The condenser will cool the gas, thereby condensing the excessive moisture in preparation for its subsequent removal. The condenser is of ample proportion to suit local conditions and ensures complete cooling, provided that sufficient water supply is maintained.
The IIGAS drier is charged with calcium chloride. This absorbs the moisture in the gas. In case a certain amount of moisture is necessary to enable the chemical purifier to function effectively, a by-pass is provided to allow part or whole of the gas to be directly admitted into the chemical purifier.
This consists of two layers of regenerative chemicals, which remove additional impurities. The purifying agent may be reactivated for re-use by the atmosphere air. For continuous operation, one extra charge of chemicals can be kept in open wooden trolleys.
The equipment is installed between the chemical purifier and Acetylene compressor, which helps to remove impurities from the gas if any.
This consists of a battery of three high-pressure vessels. The first is filled with metal filler, while the second and third are filled with anhydrous calcium chloride. It is very important that the high-pressure drier is fully filled up with Calcium Chloride, as any void in the high-pressure area is against the required safety.
This consists of a battery of filling connections to connect to the gas cylinders. Non-return valves are provided in various sections of the pipeline to the filling manifold. These non-return valves are extremely important for the safe operation of the plant and should be periodically examined. The manifold should also be periodically cleaned to remove rust and scales, (iron rust rushing through the pipeline at high speed could generate a spark and cause a fire). The cylinder filling pigtails (flexible hose pipes) should also be periodically cleaned to ensure that they do not burst during the filling operation, (if they do burst, a fire could occur due to sudden discharge of Acetylene).
DETAILS OF OUR PLANTS
|Maxinum Bar Operating Pressure||1.30|
|Minimum Guaranteed Efficiency||94%|
|Hopper Capacity||250 KG|
|Water required per hour at 2 Bar in M³/Hr for entire plant||3|
|Connected load except Water Pump & Light & Fan||8 KW|
|Conforming Specifications/ Directive||IS 8471 IS 11006 IS 15190 UL-408 TRAC-203 NFPA - 51A 97/23/EEC 98/37/EEC 73/23/EEC 89/236/EEC 95/16/EEC 94/9/EC80ATEX|
|Power Supply||380 ~ 440 Volts, 3 phase,50 hertz (can be changed as per customer requirements.)|